The CHLOR-CLEAR™ device is intended to evacuate (remove) liquid Chlorine which may be trapped in the UPPER Eductor Tube of a Chlorine Ton Container prior to changing containers. This is to prevent the introduction of liquid Chlorine into a gas chlorinator system whenever a new Ton Container is brought into service.
When a chlorinator system is operating at high flow rates, liquid Chlorine can bypass drip legs or traps and enter the chlorinator system, possibly causing serious damage. The CHLOR-CLEAR™ device prevents liquid chlorine, which may become trapped in the upper educator tube inside the ton container, from entering the chlorinator system by using a disposable nitrogen gas cartridge to force any trapped liquid chlorine back into the ton container.
Liquid chlorine can cause damage to some brands of gas chlorination equipment and leaves behind various residues, sediment and impurities when it evaporates in the vacuum areas of the chlorinator. These impurities can cause sticking and/or plugging of orifices which necessitates frequent cleaning, if not replacement of parts. Use of the CHLOR-CLEAR™, before attaching your gas chlorination equipment to a new ton container, will eliminate these problems before they even have a chance to start.
Upon ordering you will be contacted with an estimate based on your unique specifications. For immediate assistance, you may call 205-669-4535 or email firstname.lastname@example.org.
Check out the video below to see more about how it works!